9.06.11.CA-NEWS (KZ) — An accident in the Kyrgyz electric power system by short-term constraints in southern Kazakhstan. The press-service of Kazakhstan Electricity Grid (KEGOC).
According to the press service, June 8 at 14:49 in the Kyrgyz energy system abnormally disconnected 500kV overhead line A-509 "Toktogul — Frunze." Considering a repair scheme for 500 kV overhead line A-504 "Toktogul — Lochin" there was a decrease (loss) generation Toktogul from 700 MW to 0 MW.
"The actions of the emergency control in the southern zone of the Unified energy system of Kazakhstan was limited consumption equal to 195 MW (Kazphosphate 105MVt, Ontustik Zharyk 72MVt, KOREK 18MVt)," — said in a statement.
In KEGOC reported that power supply is restored the system operator in full at 15:17. Emergency Situation in the Kyrgyz energy system is normalized at 15:39 inclusion line 500kV overhead line A-509 "Toktogul — Frunze."